As John points out likely culprits are the fuse or the relay.
A competent service guy should be able to fix it. Plan B would be to bypass the relay and add a fast breaker external to the brick. That would cost less than a new brick. Most all the electronics pictured are there to sense over current and trip the relay. By bypassing the relay you just have an 18 volt transformer without a circuit breaker.